Talking Solar (405W) from old MH and putting in 07 Bounder. My question is I have to go 25 feet with #2 cable from combinder box to Controller (TriStar 45). Will #2 Cable be OK or do I need larger Cable? I have read so many pages on Solar installation and still lost. Thanks
RET ARMY 1980,DW Donna,"Tiny" (furkid) . Class A, 2007 Bounder 35E, Ford Chassis w/Steer Safe, 4SAMS 6Volts, 525W Solar , TriStar 45 Controller, Yamaha 2400, TOW: Honda CRV. Ready Brake. "Living Our Dream". NASCAR FAN 14,18,20,11 LOVE CO & NM
You're fine and can use smaller wire as posted above. But 2 suggestions:
1. Post # panels, panel info, wire length of each panel to the combiner box, plus the 25', and the length to the batteries. You'll get more information.
2. Consider if you might instead use a MPPT controller or upgrade in the future. In that case the wiring considerations are different and you may want to use those considerations even with a PWM contoller.
With the 2ga you will have less than 1% voltage drop... You could use 6ga wire and still only have lose 2.5%.
If you haven't purchased the wire yet, you can save yourself a few bucks by using 6ga (which by the way has an ampacity rating of 102A).